- 1 emonTx V3
- 1.1 Features
- 1.2 Port Map
- 1.3 Overview
- 1.4 Power Supply Options
- 1.5 Uploading Arduino Firmware
- 1.6 Standard Operation
- 1.7 Extended Operation
- 1.8 RF Connectivity
- 1.9 Electrical Characteristics
- 1.10 Open-Hardware Design Files
- 1.11 Physical Dimensions
- 1.12 Environmental & Life Cycle
- 1.13 Disclaimer
The emontx v3 is the latest generation of the open source hardware emontx low power wireless energy monitoring node designed for measuring AC electrical power on 4 different (household/building) circuits using non-invasive clip on CT current sensors and an AC-AC Voltage adaptor to provide a voltage signal for full real power and powerfactor calculation.
- Emontx v3 can measure real power, apparent power, power factor, rms voltage and current on 4 different mains circuits, it also has inputs for temperature and humidity sensing.
- Pre-assembled SMT design
- A single AC-AC adapter can now be used to power the emonTxV3 and provide AC voltage measurement
- 4x CT current sensing inputs
- An on-board 3x AA battery option
- Flexible choice of RF radio module and removable microcontroller
Power Supply Options
There are four ways to power the emonTx V3:
- USB to UART cable - only recommended for short periods while programming, it's recommended to remove all other power sources
- 5V DC Mini-USB cable - remove jumper JP2 when powerinf via DC if AC adapter is preset
- 3 x AA Batteries - remove jumper JP2 when powering via DC if AC adapter is preset
- 9V AC-AC power adapter - with jumper JP2 closed
Powering via DC (1-3)
When powering the emonTx V3 via DC (1-3) (and running the main emonTx firmware (emonTxV3_RFM12B_DiscreteSampling)) the emonTx V3 will take Apparent Power measurements, measuring only current, assuming the Power Factor of 1 and Vrms to be 230V, power saving mode will also be implemented, going into sleep mode in between readings (default every 10s) to save battery power.
The red LED indicator with illuminate for a couple of seconds then extinguish never to flash again if powering from a DC source. If the LED flashes multiple times at startup this indicates the emonTx is detecting an AC waveform this can happen if an AC adapter has just been removed, hit the reset button if this occurs. When powering the unit via 5V USB/battery it's advisable to remove the JP2 jumper if AC adapter is present.
Powering via AC (4)
A nice feature of the emonTx V3 is the ability to use an AC-AC adapter to power the unit at the same time as simultaneously providing an AC voltage waveform sample. If the emonTx V3 detects the presence of an AC waveform (AC adapter connected) at startup it will automatically implement Real Power and Irms measurements by sampling the AC waveform. Real Power is what you get billed for and can sometimes (depending on the appliances connected to the circuit being monitored) vary significantly from Apparent Power see Building Blocks for more info on AC power theory. For best power monitoring accuracy we recommend powering with an AC-AC adapter whenever possible.
Using the AC voltage waveform for reference also enables the emonTx to monitor the direction of the current flow, this is important for solar PV monitoring, if you notice a negative reading when you were expecting a positive one, flip the orientation of the CT. The red indicator LED will flash at startup then flash once every 10's to indicate that an AC waveform has been detected. Sleep mode will be disabled to keep a more consistent power draw on the AC circuit.
Important note regarding powering with AC: powering via AC is only recommended for standard emonTx operation without auxiliary sensors (apart from a single DS128B20 temperature sensor) or equipment (e.g. relay modules) connected. If the current draw exceeds 20mA the AC voltage waveform sample will be effected, effecting the reading accuracy of the emonTx. To avoid damage to the emonTx V3 circuits the current drawn from the AC circuit should never exceed 60mA See technical wiki for more info. If more than 20mA of current is required it's recommended to remove jumper JP2 and power the units via 5V USB. If an AC adapter is connected it will only be used to provide an AC sample when JP2 is removed.
Uploading Arduino Firmware
The emonTx V3 with the RFu328 uses the ATmega328 microcontroller (same as Arduino Uno) and comes with the Optiboot (Arduino Uno) serial bootloader installed. This makes it super easy to upload new code to the emonTx V3 from the Arduino IDE.
A USB to UART cable is required to upload new Arduino firmware sketches
Start by downloading the firmware, libraries and setting up the Arduino programming environment by following this guide:
Once complete the emonTx V3 firmware location should be navigable from within the Arduino IDE by going to:
File > Sketchbook > OpenEnergyMonitor > emonTxFirmware > emonTxV3
These are the examples available on GitHub so far for the emonTx V3:
- emonTxV3_RFM12B_DiscreteSampling - MAIN FIRMWARE Nov 2013
- Auto detection of AC-AC adapter sets Apparent Power / Real Power Sampling accordingly
- Auto detection of battery / USB 5V or AC > DC power method and sets sleep mode accordingly
- Auto detection of CT connections and samples only from the channels needed
- Auto detection of remote DS18B20 temperature sensor connection
Note: some of these have not been tested extensively, others are incomplete or lacking full functions
Note: some of these have not been tested extensively, others are incomplete or lacking full functions
All emonTx V3 firmware is available on GitHub here: Github:emonTxFirmware
CT Energy Monitoring
A DS18B20 digital temperature sensor can easily be connected by the emonTx V3 by connecting the sensor into to the emonTx V3's screw terminal block. The default firmware supports auto-detecting one DS18B20. Many DS18B20's can be connected but this will require change of Arduino firmware.
In order to save power when running off batteries the emonTx V3 supports switching off the DS18B20 in between readings and performing the temperature conversion while the ATmega328 is sleeping. To do this the DS18B20 power pin is supplied with 3.3V from Dig5, this digital pin is switched off between readings. The data connection from the DS18B20 is connected to Dig19, this I/O pin has got a 4K7 pull-up resistor on-board the emonTx V3 PCB as required by the DS18B20.
To connect an external DS18B20 to the emonTx V3 screw terminal block connections are as follows
|Screw terminal pin||DS18B20 Connection|
|3 - GND||GND (Black)|
|5 - Dig5||Power (Red)|
|6 - Dig19||Data (White)|
Utility Meter Interface
Optical Pulse Counting
Many meters have pulse outputs, including electricity meters: single phase, 3-phase, import, export.. Gas meters, Water flow meters etc. The pulse output may be a flashing LED or a switching relay (usually solid state) or both. We recommend using optical interface as this decouples the monitoring equipment from any high voltages.
In the case of an electricity meter a pulse output corresponds to a certain amount of energy passing through the meter (KWhr/Wh). For single-phase domestic electricity meters (eg. Elster A100c) each pulse usually corresponds to 1 Wh (1000 pulses per kwh).
The emonTx V3 has got one interrupt input (IRQ 0, Dig2) which can be used for pulse counting. This is broken out on terminal block port 4
Read more about pulse counting on the OpenEnergyMonitor Buillding Block pagers here
emonTx V3 Hardware Connections
Connect the pulse input into emonTx V3 terminal block port 4 (IRQ 0 / Digital 2) If you're connecting a hard-wired pulse output you may need to add a pull-down resistor onto the emonTx V3 PCB (R31) If you're using an optical counter (e.g TSL257) you should connecting the power pin to the 3.3V or 5V (if running off 5V USB)
|Screw terminal pin||Connection|
|1||5V (if powered via 5V USB)|
|4||IRQ 0 / Dig2|
We recommend powering the emonTx V3 from 5V USB when using for pulse counting operation. Due to the additional power requirements of the optical pulse sensor battery life will be reduced compared to CT operation if powering from 3 x AA batteries.
Direct Optical Interface
if you have an Elster meter (tested with Elster 100C) the emonTx V3 with an IR TSL261R sensor can be used to interface directly with the meter protocol to read off the exact accumulated watt hours that you have generated or used. This reading can be used on it's own or to cross-check and calibrate CT based measurement. See here for original blog post
The Rfu328 sold through the OpenEnergyMonitor shop is ready setup for use with the RFM12B, just make sure you solder the RFM12B with the correct orientation if soldering it yourself: the crystal on the RFM12B should be on the same side as the tiny 16Mhz ATmega328 crystal on the RFu328. To use the RFM12B on the RFu328 a modified version of the JeeLib RF12 library has been created. This is called the RFu_JeeLib see GitHub readme for the modifications which have been undertaken. Once using the RFu_JeeLib the RFM12B on the RFu348 can be used exactly the same as before, all code written for the emonTx V2, JeeNode etc should work just fine using using the RFu_JeeLib library.
A Ciseco SRF module can be used on the emonTx V3. The easiest thing to do is to purchase a complete RFu328 SRF setup from Ciseco.However a SRF can be used on the RFu328 purchased from the OpenEnergyMonitor shop with one small modification. The RFu328 sold through the OpenEnergyMonitor shop comes read setup for use the RFM12B, to use it with the SRF you will need to remove one SMT resistor and rotate another by 90 degress. Follow these instructions from Ciseco IN REVERSE!
SMA Antenna options
|Manufacturer||Description||Value||Package||Rapid Code||Farnell Code||RS Code|
|RF-Solutions||434Mhz Ant straight||434Mhz||SMA||542-488||1304036||542-535|
|RF-Solutions||434Mhz Ant 90 degrees||434Mhz||SMA||542-488|
|RF-Solutions||868Mhz Ant straight||868Mhz||SMA||1304037||542-551|
|RF-Solutions||868Mhz Ant 90 degrees||868Mhz||SMA||542-563|
power consumption, absolute max values
Open-Hardware Design Files
Proudly open source, the hardware designs are released under the Creative Commons Attribution-ShareAlike 3.0 Unported License:
All the Design files for the emonTx V3 are hosted on Git based SolderPad, see: http://solderpad.com/git/openenergymon/emontxv3
PCB: 100mm x 80mm
Download: Extruded Aluminium Case Datasheet